OUR TECHNICAL SPECIFICATIONS
Capacity of destruction in weight:100kg/h
able to operate not less that 12 hrs/day
must be able to destruct all combustible wastes produced
by hospitals,private clinics,laboratories,institutes ect
Types A,B,C,D AND Efor medical waste
PYROLYTIC Combustion,by Controlling the gasifiaction of waste
must avoid the release of black smoke and fine dust,during the loadings.
It should be ablke to hold the emission in the second burn
able to reduce the volume of waste by 98%
compeltely free from visible smokeand offensive odours
lower calories power LCP of this waste will be 3500 kcal/kg
minimum temperature 850c and max 1400C,post combustion less than 1100C
Internal diameter of the chemney: 0/400 and its height 8m
The volume of the combustion chamber 1.1200L
Diamension of the Door for the loading in CM 70*70
Burner opeartion should be automaticOn/Off
Fuel : Diesel
The Supplier must provide necessary information for the best of the installation
A combustion chamber of waste,perfect tight door for
A Burner of lighting which the use is limited to the ignition of waste.
Frontage of loading with doors seals gone up up on hinges,wheel,of screw plug,flexible joint,
and stuffing insulating out of refractory.
the insulation of the combustion chamber should be composed of refractory bricks,having I high content of
alluminuim and isulates bricks in order to assure a minimum temperature on the outside sheet metal.
Composition of the factory;
Thickness more than 100mm
Nature : 42% of A1203
Insulate in fibrous pannels
Burner of light waste with fuel standard mono-bloc casting guidling plunning flame,lighting
Plate of combustion I Carborundum,avaoidingthe fixing of glass of slags.
A chamber of paosting ,a divece of air intel of the gases burn.
Cracass in strong sheet steel with support of connection.
Composition of the refractoiry
Refractory concrete:Thickness not more than 150mm,nature 65% of a1203,insulating in fibrous panel:
thickness not more than 85mm,nature : calcium
Burner fuel,mono-bloc casting guiding type with horizontal flamelighiting and
A secondary injection of air to ensure perfect oxygen content.
a acontrol box ensuring the compete cycle of oxygen.
Fan: Electro ventlator distributing the secondary air,the regulation of the air flow being carried out by valves and following the control of the automatic
Control and regulations
control box watertight to dust,including:
A switch circuit breaker for each engine
Aswitch with adjustable temporization for the regulation of each burner
A regulation with digital watching for the temperature of combustion
A switch regulator with dogital watching for the temperature of postcombustion
The de-ashing must be done in the bottom of combustion chamber or the dishing should be automatic or manual batch de ashing
Process filtering system scruber to be mentioned as option
Emision standard compliance BS 3316 OR EQUIVALENT STANDARD
Capacity to treat plastic not less than 40% by weight
CE Manufacturing Complience BS EN 746-2-1997
batches of spare parts of its first urgency and consumable of the incinerator.
The installed incinerator must bear a one year guarantee
Supplier must perform an onsite installation of the incinerator
The technical training of operators will have to be provided and given by a technician from the factory ;it will consist
of curative and preventive maintanance and the use of of machine etc.
Civil WORK AND ANY OTHER VRELATED SERVICES FOR THE INSTALLATION AND TRAINING OF OPERATORS
INCLUDED IN THE INCENARATOR’S PRICE.
House of incinerator inclusive in offer the house must have facilities for hand washing and firefighting
This materials and equipment must include in the shed of the incinerator: foundation in rubble stone,isolation roofing against humudity,elevation
with brick of 20cm bloc cement continuing lintel in reinfored contrete;steel frame(charpente en metal); roofing in sheet B.C.A 28 BG
METAL GUTTER,SANITARY INSTALLATION(*WASH BASIN), soakway pit of 20m of depth;ash pit of 30m3,electrical installation:plinth with cement;
smooth roughtcast of walls (interior and outside cement;20metal doors;email paintings inside and latex painting outside the house
on walls and on doors,roofing limit;measures for thid specifications will depend on the size of the incinerator which determine the size of the shed
of the incinerator etc